Flexible Cable/CCA Cable 14AWG-1250mcm/ CCA Wire
One of the biggest cable manufacturer in China,
cheaper price&good quality
sales in Middle East,Africa,Chile,Brazil,bolivia
This cable is intended for fixed installation in wind turbine towers. Good resistance to temperatures, oils, ozone and fire. Not for use on DC power circuits.
Nominal voltage: RHH/RHW-2 2000V UL
Conductor: The conductor shall be a flexible Copper Clad Aluminum (CCA), an electrical conductor that has an outer sleeve of copper metallurgically bonded to a solid aluminum core. The combination of these two metals makes it uniquely suited to many electrical applications where weights to electrical conductivity issues are important. This bimetallic wire is much lighter than copper and only slightly heavier than bare aluminum. The density of CCA is about 35% lighter than copper. CCA conducts like copper for AC frequencies. This product meets or exceeds the minimum requirements set forth in ASTM B 566 04.
Separator: A suitable tape separator between the conductor and insulation.
Insulation: Ethylene-propylene rubber (EPR) type EP, meeting UL and ICEA requirements for 90ºC.
Jacket: A heavy duty, thermosetting CPE in accordance with ICEA S-95-658 NEMA WC70
Jacket Color: Black
Print Legend: TOWERGUARD CCA™ (SIZE AWG OR KCMIL) CU CLAD AL DLO UL 217923 RHH or RHW-2 2000V SUN RES OIL RES PATENT PENDING (SEQUENTIAL FOOTAGE MARKER)
ICEA S-95-658 / NEMA WC70
UL Standard 44
ASTM B 566
ASTM B 172
35% less expensive than copper cables with equal ampacity
Flexible cable design – TowerGuard CCA™ can bend to a radius of 6 times the O.D. without impairing the insulation.
90°C (dry) 90°C (wet)
Ozone, sunlight, oil, grease, weather, water, chemical and abrasion resistant jacket
Surface printed for easy identification
35% lighter weight and easier to install than copper cables with equal ampacity
No scrap value (theft deterrent)
Sequential footage markers
*Ampacity is calculated based on a single conductor in free air with a 90°C conductor temperature and 30°C ambient, per 2005 NEC, Table 310-17
**Ampacity is calculated based on 3 conductors in a duct with a 90°C conductor temperature and 30°C ambient, per 2005 NEC, Table 310-17
and, ccs conductor meets or exceeds the following ASTM,BS,DIN, ABS….