Electric Nylone Wire
1Type THHN/THWN2 building wire is intended for general purpose applications as defined by the National Electrical Code (NEC)Type THHN-THWN-2 is permitted for new construction or rewiring for 60 volt applications. Applications requiring Type THHN or THWN-
2, the conductor is appropriate for use in wet or dry locations at temperatures not to exceed 90°C or not to exceed 75°C in oil or coolants. Applications requiring Type MTW conductor is appropriate for use in dry locations at 90°C, or not to exceed 60°C in wet locations or where exposed to oils or coolants. Applications requiring Type AWM conductor is appropriate for use at temperatures to not exceed 105°C in dry locations.
Nylon outer jacket for easy pulling. VW-1 rated 14 AWG – 8 AWG. All sizes are rated gasoline and oil-resistant II.
A tough, polyamide, Nylon outer covering per UL-1063 and UL-83.
Underwriters Laboratories Standards UL-83, UL-1063, UL-758
AWM Spec 1316, 1317, 1318, 1319, 1320, 1321
ASTM Stranding Class B3, B8, B787
Federal Specification A-A-59544
Canadian Standards Association C22.2 No. 75
NEMA WC70/ICEA S-95-658
Institute of Electrical and Electronics Engineers
UL Listed Types TFFN, THHN/THWN
Insulation: PVC (Poly Vinyl Chloride) with Secondary Nylon Jacket
Conductor: Bare Copper Voltage Rating: 600 Volts