Copper Aluminum Conductor XLPE Insulated PVC Sheathed Overhead Underground Armoured Electric Wire Power Cable
XLPE insulated power cable is used to transmit and distribute power for the power transmission and distribution system of 35kV or lower. It is generally applied in the fields of power, construction, mine, metallurgy, petrochemical industry and communication. It completely replaces the oil immersed paper insulated power cable and partiallyreplaces the PVC insulated power cable.
BS EN IEC , etc..
|Cu core||Al core|
|XLPE insulated, PVC or PE Sheathed Power Cable||For laying indoor, tunnel, channel and underground. Unable to bear external mechanical force, but bear the traction force during laid|
|XLPE Insulated, Steel Tape Armored, PVC or PE Sheathed Power Cable||For laying indoor, tunnel, channel and underground. Able to bear external mechanical force, but unable to bear large pulling force|
|XLPE Insulated, Fine Steel Wire Armored, PVC or PE Sheathed Power Cable||For laying in shaft with large difference of level. Able to bear external mechanical force and moderate pulling force|
|YJV42 YJV42||YJLV42 YJLV42||XLPE Insulated, Thick Steel Wire Armored, PVC or PE Sheathed Power Cable||Able to bear positive pressure and pulling force|
Note: "ZR-" includes ABC three kinds of flame retardent cables, which are respectively indicated in "ZRA-" or "ZRB-" "ZRC-". For example: "ZRB-YJV", "ZRA-YJV22".
Rated Voltage, No. of Core and Range of Sectional Area
|Rated voltage (kv) |
Sectional area (mm2)
No. of core
Main Technical Quota
1. DC resistance: conductor resistance of finished cable at 20ºC per kilometer is not more than the following values.
|Nominal section area (mm2)||1.5 2.5 4 6 10 16 25 35 50 70 95 120 150 185 240 300 400 500 630 800|
|Copper core||12.1 7.41 4.61 3.08 1.83 1.15 0.727 0.524 0.387 0.268 0.193 0.153 0.124 0.0991 0.0754 0.0601 0.0470 0.0366 0.0283 0.0221|
|Aluminum core||18.1 12.1 7.41 4.61 3.08 1.91 1.20 0.868 0.641 0.443 0.320 0.253 0.206 0.164 0.125 0.100 0.778 0.0605 0.0469 0.0367|
2. Voltage Test and Partial Discharge Test
|Rate voltage Uo (kv) |
|0.6/1||1.8/3||3.6/6||6/6 6/10||8.7/10 8.7/15||12/20||18/20 18/30||21/35||26/35|
|Partial discharge test||Test voltage||–||–||6.2||10.4||15.1||20.8||31.1||36.3||45|
Packing in wooden drums,steel wooden drums or as customer’s requirement.
We have a professional sales team with each of them has engaged in this job for 3-10 years, so that we can provide the comprehensive and professional technology for you. With the perfect quality and after sales service, till now we have exported to more than 80 countries, welcome to visit us and establish win-win establish relationship!
As first rank of the cable supplier in China, we have obtained CCC, ISO9001, ISO14001, OHSAS certificates, passed the SGS and BV test, and our brand "RMJT" be given China famous brand.
People’s Cable Group Co., Ltd. was founded in 2007, located in Zhengzhou Gongyi economic development zone. Our company has 2 factories (Zhitian factory and Zhulin factory), occupies total area of more than 300,000 square meters, with building area 230,000 square meters.
- Next: XLPE/PVC Insualtion Thw/Tw/Thhn Copper Wire
- Previous: Aluminum Conductor Steel Reinfore Cable ACSR Rabbit Conductor