6.6kv XLPE Cable with Copper or Aluminium Conductor
Advantages of Hebei Huatong Cables Group:
Top ten cable manufacturer in China
Largest manufacturer&exporter of UL listed cables in China
Annual export volume exceed USD300million
UL, CUL, CSA, TUV, KEMA, CE, BV, PSB, SABS, LLOYD’S, GL, NK, KR, ABS certificates
CNAS approved lab!
6.6kv xlpe cable :
It is used to transmit and distribute power in power transmission and distribution system of 35kV or lower. It is generally applied to the fields including power, construction, mines, metallurgy, petrochemical industry and communication in complete replace of oil immersed paper insulated power cable and in partial replace of PVC insulated power cable. Power cables for power networks, underground, outdoors and in cable ducting
Standards: BS6622, BS EN/IEC 60228,IEC60502.2
Conductor: Class 2 stranded plain copper conductor to BS EN 60228:2005 (previously BS6360)
Conductor screen: Semi-conducting material
Insulation: XLPE (Cross-Linked Polyethylene) Type GP8 to BS7655
Insulation Screen: Semi-conducting material
Metallic Screen: Individual and overall copper tape screen to BS6622
Filler: PET (Polyethylene Terephthalate) fibres
Separator: Binding tape
Bedding: PVC (Polyvinyl Chloride) Type TM1 to BS7655
Single Core: Aluminum Wire Armored (AWA)
MultiCore: Steel Wire Armored (SWA)
Sheath: PVC (Polyvinyl Chloride) Type TM1 to BS7655
Color: Red or Black
3 Using features:
1.Rated voltage: Uo/U:3.6/6kV, 6/10kV(11kV), 12/20kV(24kV), 19/33kV, 26/35kV(35kV).
2. No. of core: Single core or three cores.
3. The highest allowed operating temperature of conductor for long-term working is 90oC. In short-circuit (Max. long-term is no more than 5 seconds). The highest temperature for conductor is no more than 250ºC.
4. D.C. resistance of the conductor complies with the stipulations of 3.6/6kV, 6/10kV(11kV), 12/20kV(24kV), 19/33kV, 26/35kV(35kV).
5. The environment temperature should be no lower than 0oC when lay. Otherwise it should be preheated.
6. The cable is laid without horizontal drop limit.
7. Working Frequency Voltage Test: 3.5Uo/5min without puncture.
8. Partial Discharge Test: The discharge volume should be no more than 10pC under 1.73Uo for the cable.
HeBei huatong wires&cables Group Co.,ltd.It was established in 1993, we are JV with Furukawa(Japanese company) for rubber serious cables and JV with Riken(Japanese company) for elevator cables.
Besides these,our submersible oil pump cable and shipboard cable are very influential in domestic, and, the traditional cables are also produced such as PVC powercables, XLPE power cables, ABC cables, wires, control cables, screened cables,communication cables, conductors.We areOEM for many USA, Europen, Australia cable company,70% of our products are exported, most customers are from developed countries. We got ISO,UL,TUV,
KEMA,CE and many other certifications.
- Next: XLPE Insulated Polyolefin Sheathed Kyjyp Shield Control Electric Wire & Cable
- Previous: 4-Core American Standard UL1277 Industrial Cables Xhhw Type Tc Power Cable
Similar Or Related
- No related articles