6/10 Kv Cu (AL) / XLPE / Swa (STA) / PVC Power Cable
The cables are designed for distribution of electrical power with nominal voltage Uo/U 19/33KV and frequency 50Hz. It is used to transmit and distribute power in power transmission and distribution system of 33kV or lower. It is generally applied to the fields including power, construction, mines, metallurgy, petrochemical industry and communication in complete replace of oil immersed paper insulated power cable and in partial replace of PVC insulated power cable.
BS 7835 (LSZH Version)
Conductor: Plain annealed copper or aluminium complying with IEC 60228/BS 6360. Copper
conductors shall be stranded and aluminium conductors shall be either solid or
Conductor Screen: Extruded layer of semi-conducting cross-linkable compound is applied
over the conductor and shall cover the surface completely. The minimum thickness is 0.3mm
and the maximum resistivity shall not exceed 500 Ohm-m at 90°C.
Insulation: Insulation is of cross-linked polyethylene compound XLPE (GP8) conforming to
BS 7655-1.3 or EPR (GP7), conforming to BS 7655-1.2.
|Nom. Cross- Section |
|Nom. Insulation |
|Copper Tape |
|Nom. Armour |
|Approx. Overall |