1000V Electric Building Cable PVC Insulated Aluminum Cable 5 Core 95mm2 50mm
These cables are used for electricity supply in low voltage installation system, They are suitable for installation in indoors and outdoors, in cable ducts, under ground, in power and switching stations, local energy distributions, industrial plants, where there is no risk of mechanical damage. The lead sheath brings an enhanced resistance to aromatic hydrocarbons.
The conductors shall be either of Class 1 or Class 2 of plain or metal-coated annealed copper or of plain aluminium or aluminium
alloy, or of Class 5 of plain or metal-coated copper in accordance with IEC 60228.
XLPE Insulation material and thickness shall be as per IEC 60502-1, XLPE material shall be Type A as per IEC 60502-1.
Colour Code (1)
|1 Core||Red or Black|
|2 Cores||Red Black|
|3 Cores||Red Yellow Blue|
|4 Cores||Red Yellow Blue Black|
|5 Cores||Red Yellow Blue Black Green|
|Above 5 Coreas||Black Cores with White numerals|
Colour Code (2)
|1 Core||Brown or Blue|
|2 Cores||Brown Blue|
|3 Cores||Brown, Black, Grey|
|4 Cores||Blue, Brown, Black, Grey|
|5 Cores||Green/Yellow, Blue, Brown, Black, Grey|
|Above 5 Coreas||Black Cores with White num|
Other colours can be manufactured upon request.
Assembly / Inner Covering
The inner coverings may be extruded or lapped. For cables with circular cores, except cables with more than five cores,
a lapped inner covering shall be permitted only if the interstices between the cores are substantially filled. A suitable binder
is permitted before application of an extruded inner covering. The materials used for inner coverings and fillers shall be
suitable for the operating temperature of the cable and compatible with the insulating material.For halogen free cables,
the inner covering and fillers shall also be halogen free compound.
lead or lead alloy and shall be applied as a reasonably tight-fitting seamless tube.
The seperation sheath shall be of extruded PVC Type ST2 as per IEC 60502-1, or other material refer to outer
Aluminum/galvanized steel/steel wires applied helically over the Inner Covering as per IEC 60502-1, or double
aluminum/steel tapes and copper/tinned copper wire can also be manufactured upon request.
Outer sheath shall be of extruded PVC Type ST1/ST2 as per IEC 60502-1, Polyethylene type ST3/ST7, Halogen free
compound ST8, Polychloroprene, chlorosulfonated polyethylene or similar polymers, type SE1 are also available
Any problem and inquiry pls contact with Tina
Phone number: +86-15737156317
- Next: 12/20 (24) Kv XLPE Insulated Copper Three Core Mv Power Cable
- Previous: 400V Power Cables 3 Phase 4 Core Cable 25mm for Myanmar