0.6/1kv Aluminum AAC PVC ABC Cable Overhead Cable
Triplex conductor 600V secondary type urd cable-aluminum conductor, A cable factory in China,Since 1984
400 staff,12,000 m2
Used to supply 3 phase power, usually from a pole- mounted transformer, to the user’s service head where connection to the service entrance cable is made. To be used at voltages of 600 volts or less phase to phase and at conductor temperatures not to exceed 75°C for polyethylene insulated conductors or 90°C for crosslinked polyethylene (XLP) insulated conductors.
Conductors are concentrically stranded, compressed 1350-H19 aluminum. Insulated with either polyethylene or XLP crosslinked polyethylene. Neutral messengers are concentrically stranded 6201 alloy. One conductor is manufactured with an extruded ridge for phase identification.
B-230 Aluminum Wire, 1350-H19 for Electrical Purposes.
B-231 Aluminum conductors, Concentric-Lay-Stranded.
B-232 Aluminum Conductors, Concentric- Lay-Stranded, Coated Steel Reinforced (ACSR).
B-399 Concentric-Lay-Stranded, 6201-T81 Aluminum Alloy Conductors.
B498 Zinc-Coated Steel Core Wire for Aluminum Conductors, Steel Reinforced (ACSR).
Quadruplex Service Drop cable meets or exceeds all applicable requirements of ANSI/ICEA S-76-474.
Designated sizes are : ACSR 6/1 diameter equivalent and AAC with equivalent resistivity per ASTMB-399 for 6201.Conductor temperature of 90°C for XLR 75°C for Poly; ambient temperatures of 40°C; emissivity 0.9; 2ft./sec/wind in sun. To determine current ampacity by conductor size, please consult The National Electric Code, latest edition
- Next: 0.6 / 1kv Overhead Electric Transmission Aerial Bundled Cable
- Previous: PVC Insulated Copper Conductor Building Wire