Al/XLPE/Cts/PVC, Power Cable, 6/10 (12) Kv, 3/C (IEC 60502-2)
The cable design conforms to IEC 60502 part 2. However if requested, we can separately offer guaranteed technical particulars for cables as per different international specifications or specific customer needs.
Aluminum Conductors upto 1000 sq mm will be circular compacted & stranded and shall comply with IEC-60228 Class 2.
This will be an extruded layer of semiconducting XLPE applied under simultaneous triple extrusion process over the conductor along with the insulation and the insulation screen.
This will be an extruded layer of insulating grade XLPE applied over conductor screen under triple extrusion process along with conductor screen and insulation screen.
This will be a layer of semiconducting XLPE which will be applied by tripe extrusion process over the insulation.
It will consist of a layer of copper tape applied helically with overlap over insulation screen. Other combinations of metallic screens as per customer’s requirement can also be provided on request.
An extruded layer is applied over the armour in case of armoured cables and over the laid up cores in case of unarmoured cables. Outer sheath material can be either PVC of grade ST2 or PE of grade ST7 as per IEC-60502 Part 2.
|Section||Conductor diameter||Conductor weight||Insulation thickness||Outer sheath thickness||Cable overall diamete||Cable weight||Minimum bending radius of cable (During installation)||DC resistance of conductor at 20 °C (Maximum)|
- Next: Al/XLPE/Cts/PVC/Awa/PVC, Power Cable, 6/10 (12) Kv, 1/C (IEC 60502-2)
- Previous: Al/XLPE/Cts/PVC, Power Cable, 8.7/15 (17.5) Kv, 1/C (IEC 60502-2)